PD Meter Types: Rotary Meter and Diaphragm Gas Meters
The positive displacement or PD meter is considered being a traditional gas technology, and even in the face of new technologies, the rotary meter, and diaphragm gas meter, are still widely used for utility billing applications or custody transfer of natural gas.
PD Meter Operation Principle
Positive displacement meters are volumetric flow meters and measure a volume of fluid by displacing components within the meter. In a PD meter, the gas flows into a chamber of known volume. The flow rate is determined based on the number of times the chamber is filled and emptied as the gas flows over time.
Types of Positive Displacement Meters
Examples of positive displacement flow meters are oval gear, rotary, piston, nutating disc, diaphragm, and helical. These meters are used for residential, commercial, and industrial applications and widely employed in utility gas flow measurement, often competing with turbine flowmeters.
Overall, however, positive-displacement meters excel over turbine meters when measuring low flow. As a rule, a turbine meter may not turn if the gas stream drops below 15% of the rated flow of the meter, yet, turbines surpass PD meters in larger lines when the flow is steady and high.
Diaphragm and Rotary Gas Meters
Both diaphragm and rotary meters are the more popular PD meters for natural gas flow measurement for fiscal metering. While today there appears to be an inclination toward rotary meters, diaphragm meters still have a substantial market share.
Industrial plants also use PD meters for submetering, not for measuring process gas in the manufacturing process. However, some PD flowmeters are being replaced with new technology meters in the industrial gas environment.
Positive displacement meters are relatively low cost, long-lasting, and reliable, making them the choice for gas utilities billing meters. Part of this is attributed to slow industry approval of new technology (Coriolis, magnetic, ultrasonic).
There is a trend of replacing retiring diaphragm meters with rotary meters since they are smaller, lighter and permit the users to upgrade measurement capability. Rotary meters handle higher volumes and pressure over diaphragm meters, yet like turbines, have restrictions in low-flow conditions. Also, rotary meters are used in non-utility gas flow in industrial environments.
Since PD meters have moving parts, they are subject to wear and tear and require periodic maintenance. Dirty gas is problematic for PD meters, and because the structural design needs an obstruction in the gas flow, a pressure drop is created. Also, PD meters can also be bulky, particularly in larger sizes.
This post is part of a continuing series on gas flow meters. Perhaps you may be interested in: