What are the natural gas odorization requirements?
What are the natural gas odorization requirements? The regulations are published below, but what do they all mean?
Natural Gas Odorization Requirements
Natural gas in its unprocessed state is odorless yet combustible. Odorization is the process of adding an odorant to a gas so that it smells to alert a bystander that natural gas is present. This process is a critical stage to ensure the safety of people.
Under the Department of Transportation (section 192.625), the federal government requires combustible gas transported by pipeline to meet a minimum odorization standard. A distribution line and transmission line (exceptions noted in the regulations below) must contain odorant at 20% of the lower explosive limit so that a person with a “typical” sense of smell can detect it. Learn more in “What is natural gas odorization?”
PART 192: TRANSPORTATION OF NATURAL AND OTHER GAS BY PIPELINE: MINIMUM FEDERAL SAFETY STANDARDS
Subpart L: Operations
192.625 – Odorization of gas.
(a) A combustible gas in a distribution line must contain a natural odorant or be odorized so that at a concentration in air of one-fifth of the lower explosive limit, the gas is readily detectable by a person with a normal sense of smell.
(b) After December 31, 1976, a combustible gas in a transmission line in Class 3 or Class 4 location must comply with the requirements of paragraph (a) of this section unless:
(1) At least 50 percent of the length of the line downstream from that location is in Class 1 or Class 2 location;
(2) The line transports gas to any of the following facilities which received gas without an odorant from that line before May 5, 1975;
(i) An underground storage field;
(ii) A gas processing plant;
(iii) A gas dehydration plant; or
(iv) An industrial plant using gas in a process where the presence of an odorant:
(A) Makes the end product unfit for the purpose for which it is intended;
(B) Reduces the activity of a catalyst; or
(C) Reduces the percentage completion of a chemical reaction;
(3) In the case of a lateral line that transports gas to a distribution center, at least 50 percent of the length of that line is in Class 1 or Class 2 location; or
(4) The combustible gas is hydrogen intended for use as a feedstock in a manufacturing process.
(c) In the concentrations in which it is used, the odorant in combustible gases must comply with the following:
(1) The odorant may not be deleterious to persons, materials, or pipe.
(2) The products of combustion from the odorant may not be toxic when breathed, nor may they be corrosive or harmful to those materials to which the products of combustion will be exposed.
(d) The odorant may not be soluble in water to an extent greater than 2.5 parts to 100 parts by weight.
(e) Equipment for odorization must introduce the odorant without wide variations in the level of odorant.
(f) To assure the proper concentration of odorant in accordance with this section, each operator must conduct periodic sampling of combustible gases using an instrument capable of determining the percentage of gas in air at which the odor becomes readily detectable. Operators of master meter systems may comply with this requirement by?
(1) Receiving written verification from their gas source that the gas has the proper concentration of odorant; and
(2) Conducting periodic “sniff” tests at the extremities of the system to confirm that the gas contains odorant.[35 FR 13257, Aug. 19, 1970]
Who are we?
You may also be interested in:
What is odor fade? What causes odor loss in odorized natural gas?
Smelling natural gas is a warning–there is a gas leak. It’s not foolproof. What is odor fade? What causes odor loss of odorized natural gas? Read More.